IESNA:LM-63-2002
[TEST]P579777
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (G2-2106-266-2)
[TESTLAB]COOPER LIGHTING SOLUTIONS
[ISSUEDATE]9/9/2021
[MANUFAC] COOPER LIGHTING SOLUTIONS - HALO COMMERCIAL (FORMERLY EATON)
[LUMCAT]HC410D010-HM40525930-41NDH
[LUMINAIRE]HALO COMMERCIAL 4" ROUND, NEW CONSTRUCTION FRAME, WITH 4" NARROW DISTRIBUTION, HAZE TRIM
[LAMP] (1) HIGH LUMEN LED 90CRI / 3000K CCT
[DRIVER]ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTE]DATA SHOWN IS ABSOLUTE FOR THE SAMPLE PROVIDED
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]864
TILT=NONE
1 -1 1 37 1 1 1 -0.333333 -0.333333 0
1 1 9.9
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
908.6 899.8 888.7 866.2 833.2 799 764.2 722.5 675.2 627.3
576.3 520.9 458 386.5 312.4 242.7 182.3 133.1 97.1 69.6
49.7 34.3 21.2 13.7 10.6 8.8 6.8 5 3.8 3.1
1.8 1.3 1.3 0.6 0.6 0.6 0
