IESNA:LM-63-2002
[TEST]P592623
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (G2-2106-266-2)
[TESTLAB]COOPER LIGHTING SOLUTIONS
[ISSUEDATE]9/9/2021
[MANUFAC] COOPER LIGHTING SOLUTIONS - HALO COMMERCIAL (FORMERLY EATON)
[LUMCAT]HCC4S15D010MW-HM40525850-41NDH
[LUMINAIRE]HALO COMMERCIAL 4" ROUND, NEW CONSTRUCTION FRAME, WITH 4" NARROW DISTRIBUTION, HAZE TRIM
[LAMPCAT]CYLINDER
[LAMP](1) HIGH LUMEN LED 80CRI / 5000K CCT
[DRIVER]ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTE]DATA SHOWN IS ABSOLUTE FOR THE SAMPLE PROVIDED
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]1424
TILT=NONE
1 -1 1 37 1 1 1 -0.333333 -0.333333 0
1 1 14
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
1497.3 1482.9 1464.5 1427.5 1373.2 1316.8 1259.3 1190.7 1112.7 1033.8
949.6 858.3 754.7 636.8 514.8 400 300.5 219.4 160 114.8
82.1 56.4 34.9 22.5 17.4 14.3 11.3 8.2 6.1 5.1
3.1 2 2 1 1 1 0
