IESNA:LM-63-2002
[TEST]P583280
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (G2-2105-241-5)
[TESTLAB]COOPER LIGHTING SOLUTIONS
[ISSUEDATE]9/16/2021
[MANUFAC] COOPER LIGHTING SOLUTIONS - HALO COMMERCIAL (FORMERLY EATON)
[LUMCAT]HC607D010-HM60525827-61MDH
[LUMINAIRE]HALO COMMERCIAL 6" ROUND, NEW CONSTRUCTION FRAME, WITH 6" MEDIUM DISTRIBUTION, HAZE TRIM
[LAMP] (1) HIGH LUMEN LED 80CRI / 2700K CCT
[DRIVER]ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTE]DATA SHOWN IS ABSOLUTE FOR THE SAMPLE PROVIDED
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]833
TILT=NONE
1 -1 1 37 1 1 1 -0.5 -0.5 0
1 1 8
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
760.6 757.1 757.1 751.9 740.6 727.7 711.9 688.3 656 616
571.4 520.8 463.7 399.7 323.9 244.5 175.2 121.1 85.8 61.7
44.1 31.2 20.6 14.7 11.8 9.4 7 5.9 4.1 2.9
2.4 1.8 1.1 0.6 0.6 0 0
